Tuesday, May 28, 2013
NOTE: This only affects sites built with CMSMS, if your site is not built with CMSMS please ignore Announcing CMSMS 1.11.7 - Genovesa May 25, 2013 Hello folks. This is a security release of your favorite flexible, powerful, and proactive content management system. The CMSMS Dev team considers security issues to be a top priority, and tries to fix security vulnerabilities as...
Tuesday, February 19, 2013
Greetings, Due to an issue/failure with the switch on this rack we would like to notify you of the upcoming emergency maintenance. We do not anticipate more than 30 minutes of downtime for each individual server. During this maintenance, kookaburra server will be moved to a newly configured rack. many thanks Ian
Monday, January 28, 2013
Due to massive power outages in brisbane the brisbane sales office has been without phone or email access since Late Sunday. All Server Data centres and web and email support have been unaffected. Normal Sales support has returned now many thanks Ian
Sunday, November 18, 2012
This morning at approximately 10:33am our datacentre experienced a fault with the power switching gear due to external power fluctuations. The UPS' protected the site and discharged. Power was lost to all cabinets at this time. The NOC are speaking with our vendors and our electrical contractors to identify a cause and prevent this kind of incident in the future....
Thursday, November 1, 2012
There will be a php upgrade and mysql upgrade on Kookaburra server starting at approx 10pm QLD time There many be intermitent downtime as this progresses thanks ian
Wednesday, October 31, 2012
This morning the Possum.hostingoz.net.au server based in brisbane experienced rolling outages, this cause is being investigated but services are back on line. The issue here was involving connecting a backup service to this server, which caused the server to be seen as offline in some cases Our apologies for this outage. This new server is being brought online to increase our...
Friday, October 26, 2012
Our Brisbane data centre has experienced a large inbound DOS which saturated our inbound provider links. We have worked with our upstream providers to block this attack. Connectivity has been fully restored, however higher than normal packet loss is being experienced. We hope to have this issue fully resolved soon. A full incident report will be...
Saturday, October 6, 2012
We Will be undertaking work on the kookaburra server to improve its stability starting early saturday night. More updates in the announcements area
Wednesday, October 3, 2012
A issue with Kookaburra server is being worked on at the moment Issue was resolved 10.15 thanks
Tuesday, April 10, 2012
hello † Kookaburra server has been upgraded to appache v2.x and php version to 5.3.10 If you have any issue please open a support ticket (suppor @ hostingoz.com) Many Thanks HostingOZ.com Server Support Team
Powered by WHMCompleteSolution